Our tech arrived at the property to see what you saw in the before pictures. His report showed he found the 1.5″ main shut off valve was buried under ground. And the water softener loop was cut into the main line causing the entire property to be fed through the softener. This caused salt to get into irrigation and pool, when there was already a properly plumbed in softener loop that didn’t do this inside the garage.
A main riser rebuild was required to correct this issue. In addition, the 1.5″ pressure regulating valve on the main riser has failed as the home water pressure is almost 100 psi which will cause leaks in plumbing if not corrected. So we elminiated the incorrectly plumbed in softener loop on the main riser and gave it all new copper piping. We also replaced the main shut off valve above ground, replaced the pressure regulating valve, replaced the hose bib, and reused the new vacuum breaker that was already in there.
Have you discovered problems from freezing or other plumbing problem that needs fixed? Be sure and contact us for a free, no obligation estimate. Wyman Services offers plumbing services in Anthem, Arizona as well as other areas around northern Phoenix.